| Application area
|| The enclosures are suitable for outdoor installation - harsh environment and / or outdoor.
The material is examined for UV resistance by the institute for plastics and thereby suitable for the outdoor installation during UV effect.
However the climatic influences and effects on the equipment are to be considered.
| ambient temperature
|| Average value over 24 hours + 35° C
Maximum value + 40° C
Minimum value - 5° C
| Relative humidity
|| 50% at 40° C
100% at 25° C
| Fire protection in the event of internal faults
|| Demands placed on electrical devices from standards and laws
Minimum requirements - Glow wire test in accordance with IEC 60 695-2-11: - 650°C for boxes and cable glands - 850°C for parts of insulating material necessary to retain current carrying parts in position
| Burning behavior
|| Glow wire test IEC 60 695-2-11: 960° C
UL Subject 94 V-2
| degree of protection against mechanical load
|| IK08 (5 Joule)
| Toxic behavior
"halogen-free" in accordance with the examination of the cables and insulated wires - corrosiveness of fumes - as per IEC 754-2
|| To material properties see technical data.