Mi boxes are suitable for outdoor installation (harsh environment and/or outdoor). The material is examined and therefore qualified for the outdoor installation during direct sun radiation.
However, pay attention to the climatic effects on the equipment.
Resistant to occasional cleaning procedures (direct jet)
Resistance to occasional cleaning procedures (direct rinsing) with high-pressure cleaner without cleaning additives, water pressure: Max 100 bar, water temperature: Max. 80� C, distance => 0.15 m, in accordance with IP 69K requirements, individual box without lid equipment (no box combinations), single enclosures without lid components (not any enclosure assembly), enclosure and cable gland at least IP 65.
Maximum value + 70� C
Minimum value - 25� C
Fire protection in the event of internal faults
Demands placed on electrical devices from standards and laws
Minimum requirements - Glow wire test in accordance with IEC 60 695-2-11: - 650�C for boxes and cable glands - 850�C for parts of insulating material necessary to retain current carrying parts in position
Fire protection in the event of specific risks or hazards
Demands placed on electrical installations and devices in areas and facilities subject to fire risk, e.g. DIN VDE 0100 Part 482, official regulations, VdS directives
Minimum requirements - Glow wire test to IEC 60 695-2-11: - 850�C for boxes and cable glands - 850�C for cavity wall installation - Use of fire resistant cables
Glow wire test IEC 60 695-2-11: 960� C
UL Subject 94 V-2
degree of protection against mechanical load
IK08 (5 Joule)
"halogen-free" in accordance with the examination of the cables and insulated wires - corrosiveness of fumes - as per IEC 754-2
Supplementing references regarding outdoor installation - harsh environment and / or outdoor: - The materials used for the Mi System are basically UV resistant, so that the mechanical resistance of the boxes is maintained during UV effect. Depending on the intensity of the UV effect e.g. transparent lids can become intransparent. - The top side of the boxes should be protected by a cover against weather influences such as rains, ice and snow. - Further on, also chemical influences have to be considered with the selection of the installation place - apart from the IP rating and climatic effects. - In order to keep the maximum permissible ambient temperature of the installed equipment as well as for the prevention from condensation additional measures as ventilation and/or heating may be necessary.
To material properties see technical data.
Our products are used in the following areas of application:
Companies involved in the processing of metal, wood and paper, cement factories
Agricultural and food industries
Water treatment and sewage plants, power stations and cold-storage depots
Banks and insurance buildings
Leisure and commercial centers
Hotel and ciType NEMA complexes
Hospitals and clinics
Schools and universities
Stadiums and sports centers
Gas stations and traffic infrastructure in ports, underground stations, tunnel and road construction
is the Exclusive Importer of HUMMEL products. We offer over 6,000 different Types and Sizes of RoHS Compliant Liquid Tight Strain Relief Fittings, Cord Grips, Cable Glands, Circular Connectors, Conduit System, Industrial Enclosures and Other Related Cable Management Products which are rated the best in the industry.
7374 S. Eagle Street
Centennial, CO 80112-4221 USA
Toll Free: 800-456-9012 / 303-699-1135 FAX: 303-680-5344